Data center WIBODC was launched in July 2012. It is the first professional commercial Data center in Kiev, Ukraine. Reliability of the Data center corresponds to the Tier 2 international classifier. Approximate capacity of the first server room of WIBODC is 14 cabinets with 45U capacity, in which can be placed more than 600 units of active equipment.
The total electric power of the first Data center server room is 80 kW. For each cabinet is allocated up to 6 kVA.
Automatic input power backup (ATS) production of MADEK (Ukraine) provides power management of Data center. The power supply circuit is arranged as follows: two input of ATS take inputs from different substations (one of which serves as the primary, and the secondary - as a backup), and a third input connected to a diesel generator FG WILSON (UK).
If power is lost from the primary substation (first input), automatically switches to the power from backup substation - the second input of ATS. In case of any problems at the two inputs of substations in the same, within 60 seconds automatically diesel generator starts, that can fully provides power for Data center during 11 hours without refueling.
Each cabinet is equipped with an uninterruptible power supply by APC (USA), which is able to provide work of server and network equipment in continuous mode during 20-30 minutes, which is more than enough to switch to self-powered from the diesel generator.
The cable system of Data center is structured, the cables are placed in specialized wire trays above telecommunications cabinets. For the power management of cabinets are used circuit breakers production of Schneider Electric.
The network infrastructure core of Data center - the heart of WIBODC, built based on one of the best-in-class solutions from Juniper Network.
Our diesel generator is capable of providing autonomous operation of all Data center units during 11 hours without refueling.
Mitsubishi Heavy Industries
The air conditioning system of industrial level from MHI maintains optimal temperature in hot and cold corridors of the Data center server room.
Network and communication
WIBODC located in the immediate vicinity to the fiber lines of backbone ISPs. Because of this, data center provided by two independent fiber inputs. The network infrastructure is built based on High-end class equipment from Cisco and Hewlett-Packard (USA). At the head of rack switches is the infrastructure core, built based on switch Juniper EX3300 and router Juniper MX80 (USA), which allows to provide the total network capacity of the Data center up to 80 Gbit/s. The basic units of communication infrastructure are duplicated on the principle of N+1, and the total capacity of the WIBODC channels at the moment is 4 Gbit/s, and regularly increased.